The Training Never Stops At NTC.
Check back often to learn more about upcoming NTC training opportunities and the latest news and updates affecting the fire protection and low-voltage industry.
Runner service is a service required for Proprietary Supervising Station and Central Supervising Station Fire Alarm Systems.
NFPA 72 currently recognized four methods of communication from the protected premises to the supervising station for fire alarm systems.
This post is brought to you from one of our 2021 Sponsors. The National Systems Contractors Association (NSCA) is the leading not-for-profit association representing the commercial integration industry.
Article 760.3 (Other Articles) identifies other sections of NFPA 70 that also apply to fire alarm systems.
While the Point 7 Rule can be mathematically calculated for heat detectors and applied to rectangular area and corridor applications, thankfully, the math has already been done for us in NFPA 72.
NFPA 72 requires that all points on the ceiling have a detector within a distance of 0.7 times the listed spacing of the detector.
Code Question – Is there language in the code that specifically prohibits blocking a fire alarm device (like a horn/strobe or pull station) with a bookcase?
When a ceiling surface has solid projection more than 4 inches, the distance between the projections center to center determines whether the projection is a joist or beam.
Positive alarm sequence and presignal systems delay occupant notification to allow for time for investigation of a fire. While both systems delay occupant notification, the function of the features and where they are permitted are different.
Audible notification requirements in sleeping areas were changed in the 2013 edition of NFPA 72. The 2010 edition first stated that as of January 1, 2014, audible notification appliances in sleeping area would be required to produce a 520 Hz tone.